The Standalone LPG Gas Detector detector is designed for single station using. Small and compact, the design and color makes it ideal for use in the home, small commercial properties and recreational vehicles. It is intended to detect CH4 gas.The gas detector can be mounted high (for CH4 gas). It is equipped with a sturdy mounting bracket for quick, easy and safe
Check and test the gas detector after installation.It should be tested weekly and check after re-occupation following a holiday.
Power on :The green work light starts to flicker and the warm-up time is 2 minutes .During this process, only the button responds,and other tests do not respond.lt can work normally after the warm-up is completed,and the green work light is always on before the test can be performed.
Normal: When the device is in a normal state, the green light on the power supply is on, and the other lights are off
Fault: When the sensor is in a fault state, the yellow LED of the sensor flashes slowly. After troubleshooting, the device will return to normal
Alarm: When the detected gas leakage reaches the alarm level, the red alarm light will be on and the buzzer will sound. Usually the default models are relay and pulse voltage output.
Test: Under normal circumstances, press the test button, the unit should make a sound, the three LED indicators will light up once, the buzzer will beep twice, and there will be no signal output. In order to ensure the normal operation of the gas detector, you should test it once a week
Mute: The local mute can not be used in the alarm state, but the host can only be used to mute the sound remotely.
Reset: Local reset cannot be used in the alarm state, but the host can only be used to reset all remotely, there is no output, the alarm light is off, and it enters the preheating state
Remote test: the red light flashes when the host is testing
Remote mute: when the local alarm, the yellow fault light flashes quickly when the host mutes the sound remotely